Kitchen Extract Cleaning
Do you need Kitchen Extract Duct Cleaning, and are you at risk if you do not conduct regular Kitchen Extract Duct Cleaning?
Kitchen extract systems have an increased fire, odour, and hygiene risk Kitchen Extract Duct Cleaning compared to general air ventilation systems. This is due to the grease, cooking oil and other deposits that build up over time, acting as a potential ignition source.
Cleanliness and fire safety are essential ingredients of every well-managed kitchen. A core risk element is your kitchen extract system, the perfect landing place for grease, cooking oil, and other deposits. Kitchen extract ductwork systems, if not kept clean, pose a Substantial Fire Risk.
Grease is an excellent fuel that can help a fire to spread throughout an extract system and into other areas of the building.
The Regulatory (Fire Safety) Order 2005
From April 2006 it became an offence if systems were not maintained to prevent a fire risk. In the event of personal injury or death resulting from a fire associated with a poorly maintained system (section 17 of the RRO), charges of corporate liability or manslaughter may be brought against the operator and/or responsible person.
Hydro-X Air can take the worry out of your hands with an expert kitchen extract duct cleaning service that ensures you meet your fire safety obligations under the Regulatory Reform (Fire Safety) Order 2005, minimising the risk of fire by removing grease and cooking oil deposits with a professionally conducted regular cleaning program.
Whether you are a restaurant, a hotel, or any other type of building with catering facilities, our service can be tailor-made to suit your needs at regular intervals from weekly to annual maintenance.
All of our cleaning works are compliant to the National standard of B&ES TR19 section 7. On completion our work is verified with a comprehensive photographic post clean report.
Our Hydro-X Air Post-Clean Report is designed to comply with the RRFSO, TR/19 and Technical Bulletin TB/009 and includes:
- An executive summary page that highlights the key risks.
- A clear yes or no as to whether the system was cleaned in its entirety.
- If no to the above question, the reason why it was not cleaned in its entirety and a suggested solution.
- Other hazards that have been identified.
- Micron readings for the test locations. Wet Film Thickness Testing.
- The mean (average) micron reading across all micron reading taken.
- The current cleaning frequency.
- A recommendation of a new cleaning frequency based on the micron readings.
- A sufficient number of before and after cleaning photographs of the system to give a true representation of the system condition. These should be at minimum in the seven TR/19 test locations (section 7.41) and more if the duct length exceeds 10 meters.
- A schematic diagram of the system layout showing the system that has been cleaned and any areas that could not be cleaned.
- Test locations identified on the schematic